Risk of electric shock through poor socket selection, in this example standard plastic electrical socket outlets have been fitted in an office floor
It seems quite obvious that if an electrical socket is to be fitted into the floor, it would need to be of a type that has been designed to withstand weight or impact, however someone has ignored this criteria, or has not considered the environment.
A standard plastic electrical socket outlet is designed to be mounted into a wall and would not be suitable to floor mount. The sockets in this photo would easily be broken by; the steel chair leg where the leg could become live through direct contact with the live electrical conductors.
This example was identified by a Veriserv engineer whilst carrying out an electrical fixed wiring inspection and test. The engineer would isolate the sockets and complete an “immediate report” to notify Veriserv’s customer.
The sockets should be of the type that are enclosed in a protection enclosure suitable for use on an office floor. This type of socket would normally have a lid to stop ingress of liquids should they get spilt.
Electrical equipment that is intended for use in the workplace must satisfy the safety requirements of the Electrical Equipment (Safety) Regulations 1994 and must provide a safe connection to the mains electrical supply.
The Institute of Engineering and Technology (IET) publish BS7671, IET wiring regulations seventeenth edition. Section 522.6.2 states that wiring systems shall be selected and erected so as to minimise damage arising from mechanical stress or impact during use or maintenance.
Veriserv would be happy to advise on any electrical compliance matter, or provide you with a quotation to carry out an Electrical Fixed wiring inspection and test of your premises.
Please contact us on 01543 225306 or complete our on line enquiries form.